Guangzhou fingerprint entrance guard system installation steps process steps
Entrance guard system, also known as access control system, is a kind of management personnel in and out of the digital management system.
Common entrance guard system are: password entrance guard system, non-contact IC card (
Induction IC card)
The entrance guard system, iris zhang type of biometric fingerprint entrance guard system, etc.
Entrance guard system installation to do?
Now many people want to install is not know, under the guangzhou personnel to introduce the entrance guard system of access control system installation steps process.
A 1, A front-end equipment, equipment installation, the place that take the door to install card reader.
Within the scope of the card reader induction, do not close to or contact with high frequency or strong magnetic field (
Such as overloading motor, monitor, etc. )
Grounding method, and cooperate with the control box.
B, go out to install push button.
C, electromagnetic lock installed on the door and door frame.
D, to guarantee safety and beautiful sex, controller and power box can be used on-site installation or installation in the weak current well.
On-site installation controller is the advantage of saving the use of the wire and the controller installed on elv well facilitate system maintenance and system security in the future, also can install the controller box above the card reader, near the electromagnetic lock.
Specific circumstances can choose to install way according to the customer.
2, the equipment is A central control room, control the host and the keyboard installed on the facade wall or placed on the worktable.
B, alarm device placed in alarm effect is good.
C, due to the particularity of entrance guard system, the demand for power supply of the system is good, recommended UPS power supply, the entrance guard system centralized power supply.
2 1, system installation, equipment debugging is completed, put all the access control card reader connected to the host signal, and then separate detection which entrance guard card reader, omission, false alarm.
After all this test no problem in access to the other way, so that each separate test again, all the way after confirmed all the lines connect together.
2, managers can according to the use of personnel access authorization, respectively, as part of the personnel may at any time in any place, ordinary people can only by authorized card in the authorized time in and out of the scope of authorization.
When all the normal opening of access control points and illegal opens, if there is a record to check the control center computer.
3, try to center computer and controller disconnected because of a failure or other reasons, the controller can independent record information about the control of door, after the center computer connection, whether all the information can be uploaded automatically, if you can guarantee the integrity of the information record.
4, completes the testing record.
5, and finally completed fill in the report.
Three, pipeline installation 1, installation wiring should conform to the provisions of the state & other
Electric installation engineering construction and acceptance specification & throughout;
And the related codes and regulations issued by the state.
In the thread inside the tube or trough, should be done after building plaster and ground engineering.
Before threading tube or trough should be in the water and clear out clutter.
Different systems, different voltage grade and the type of current line, should not be in the same tube or trough within the same slot.
Wire inside the tube or trough, there should be no joint or kink.
Wire connector, should be within the terminal box welding or use the terminal connection.
Small section system can splicing, splicing circle number should be in more than five turns, then tin coating, insulation bandaging.
Pipeline through building deformation joints, compensation measures should be taken, conductor cross deformation joint should be fixed on both sides, and with appropriate allowance.
Terminals in the terminal of the appropriate selection pressure or terminal board, with tin welding point on its terminal should have a label.
2, entrance guard controller installation is firm, shall not be tilted, and should be clearly marked.
Installed on the lightweight partition, reinforcement measures should be taken.
The introduction of entrance guard controller cable or wire, wiring should be neat, avoid cross, shall be fixed tightly and cable core and the department shall indicate the number of wires, and with the drawings is not easy to fade;
Terminal board and each terminal, terminal shall not exceed two root;
Cable and wire not less than 20 cm allowance shall be maintained;
Wire should tie into a bundle;
After the introduction of wire in wire threading, at into line pipe should be blocked.
3, entrance guard controller of main power supply is introduced into line should be directly connected to the power supply, it is forbidden to use the plug, the main power supply shall be clearly marked;
Entrance guard controller grounding and firm, and has the obvious mark.
4, monitoring of indoor ground bus route, specifications should comply with the design requirements.
Construction shall comply with the following rules: the surface of the ground strap should be complete, no significant damage and residual flux slag, copper strip light bus, burr, insulation aging crack not a phenomenon;
Grounding bus bar should be spread in the trough or cable central aisle, and fixed on the outer edge of the frame groove, bus should level off, can not have skewed, bending.
Bus bars connected to the frame or on the top of the machine should be firmly end;
Copper cable a hallway with bus can use screws, copper conductor bus cable a hallway, shall be binding on the rail;
Grounding installation, system of engineering construction should strictly in accordance with the design requirements.
Grounding installation, should cooperate with civil construction at the same time.